Installation example The information in this page are only a partial and summary statement of the real project. The purpose of this text is only to provide a rough track.
Reference project: PC 5202 date 2-5-2007
Insulated chamber with air conditioning plant for certified testing laboratoryes:
Brief description of the components
Data underlying the project: Net dimensions of the treated 4.5 mt. x 3 mt. h 3 mt. Load thermal equipment constant Structures Laboratory Isolate Admission to the laboratory with compass glass separation from other departments Doubles
Achievements: Minimum summer temperature refrigeration system with 20 ° C High winter heating temperature 20 ° C Maximum humidity reached 65% with humidifier Airflow total 1580 m3 / h
Consumption conditioning system: Electrical power consumption 5.7 Kw. Water Consumption 0.002 m3 / h
Structure painted panels.
Refrigerant gas compressor.
Direct expansion cooling coil.
Immersed electrode humidifiers.
Centrifugal fan with variable speed delivery.
Control unit and microprocessor control.
For the connection between the conditioner and the condenser (up to 10 meters away).
REMOTE AIR COOLED CONDENSER
Panels of polyurethane foam self-supporting film-coated aluminum.
Circular diffuser fins complete the calibration.
Panels pre-painted and insulated with polyurethane foam injected between the two sheets.
Profiles of pre-painted finish.
Floor with rubber cover.
Double glazing with air chamber.
Dimensions as dis. C5202DP1 attachment.
Made with galvanized sheet metal and plastic, insulated with polyurethane foam injected between the two sheets.
Page title: Testing Laboratories Last Update: 30-11-17